Month: July 2015
Question: Would you dump lawnmower oil into your car's engine? Probably not. Your neighbor's, maybe, but not your precious heap of a jalopy.
Same strategy holds true for your air compressor. Just like automobile oil, there are many different grades of air compressor oil to choose from, each designed to meet certain specifications.
Two main factors are involved in choosing the correct oil:
1) The type of compressor. Rotary screw or recip?
2) The environment your compressor operates in. Hot, humid temperatures? Cold? Dirty air? Clean, sterile environment?
Many compressors, many environments, many choices.
Solution? Of course there is. What's a riddle without an answer.
To help ease your pain when choosing oil for your compressor, FS-Curtis has introduced two new fluid lines: FSC-Max Fluid and Pro Fluid.
FSC-Max Fluid is our core fluid product line and comes with a bold new look. Designed to offer the highest protection for your FS-Curtis products and to operate at 100% efficiency in virtually all environments, FSC-Max will help run your unit efficiently and smoothly in various environments from food grade applications to large industrial.
How much faith do we have in the FSC-Max Fluid line? All FS-Curtis products are tested and shipped from our headquarters and plant in St. Louis, MO., using FSC-Max Fluid.
It's also the only lubricant product line that can validate FS-Curtis extended warranty programs.This is important in order to protect your investment and ensure its longevity.
Pro Fluid is a great new addition to our professional grade line of products and offers a full range of fluid choices for virtually all circumstances. It is also an ideal economical alternative for OEM replacement fluids, and a great choice when servicing industrial machinery.
For more information about which fluid is the best choice for you compressor, ask your FS-Curtis sales representative, call our service representatives at 314-383-1300 or visit our website at us.fscurtis.com
Let’s say you buy a Volvo, arguably considered one of the safest cars on the road, and you drive it 70mph into a brick wall (by the way, don’t do this, it ruins the paint job), is it the car’s fault that it may no longer run?
The same scenario applies to equipment. If the OEMs installation recommendations are not adhered to, there will be a high degree of probability that the compressed air equipment will not be reliable, will not experience the stated longevity, may require above average maintenance, may consume more electrical energy than required and may not consistently provide the compressed air quality required by production.
While it’s impossible to cover all of the things you need to consider when installing a Rotary compressor (and we hope it’s an FS-Curtis), this short article is intended to help avoid the equivalent of driving your car into a brick wall.
1) Have your system voltage measured. The most common electrical utility voltages in the United States are 200 volt, 208 volt, 230 volt, 460 volt. Electrical utilities guarantee a voltage supply tolerance of + 10%. For example, if the voltage stated supply is 230 volts it could measure at any given time from 207 up to 243 volts. Most electrical utilities attempt to hold the supply voltage to + 5%. Operating electrical motors off design or away from their nameplate voltage will generate additional heat leading to reduced motor life expectancy. The majority of induction motors, 5 hp through 600 hp supplied to the U.S. market, are 230 & 460 volts; however, 200 & 208 volt systems are becoming more popular. If a 230 volt nameplated motor is operated on a 200 to 208 volt system it will operate in an elevated heated condition leading to extremely reduced motor life. This is not a recommended practice. There are motors specifically designed for 200 & 208 volt operation. For these applications motors nameplated as such should be used.
2) Many air compressors operate into the motor service factor. As such, request the package full load operating amp draw from the manufacturer to properly size the electrical utility supply equipment (i.e., wire, electrical quick disconnect, overloads, transformers). Seek out a qualified electrical contractor in your area to assist in proper electrical utility modeling and sizing.
1) Proper placement and mounting is vital. Request a General Arrangement (GA) drawing from the OEM for each piece of compressed air equipment purchased. The GA drawing should illustrate the weight and recommended clearances to be maintained around the equipment. The floor will need to support the static weight of each piece of equipment. The equipment should be secured to the floor to prevent it from shifting around imparting stress on connected utilities such as piping, electrical and ducting. In addition, many states have adopted seismic codes mandating equipment be structurally secured to the floor. Many floors appear flat to the eye but are not flat enough to meet accepted equipment mounting practices. Many floors can be crowned (bowed) or have undulations. When securing equipment to a floor it is important to identify floor imperfections filling the air gaps with shims. When properly shimmed, the tightening of the mounting bolts will not bend or distort the equipment frame. Frame distortion will lead to excessive equipment vibration. Excessive vibration causes premature component failure which reduces machine reliability, increases cost of ownership and could potentially create an unsafe situation.
Proper clearances should be adhered to. These recommended clearances provide boundary area around the machine for safe, effective operation and servicing of the machine. This boundary area also allows adequate cooling airflow around the machine.
All piping should be properly supported as to not impart stress on the equipment. When connecting piping to the equipment pipe connector, it should be supported with proper tooling to prevent the equipment connector from turning during the piping tightening process. If the equipment receiving connector is allowed to turn (rotate) it very well could damage internal components to the equipment. Air piping should be properly sized and configured to prevent short cycling of the air compressor controls. A rule of thumb is to always use piping at least the size of the supply connection of the air compressor. If the dryer connections are larger don’t worry, the reason could be the dryer is oversized due to rerating or simply the fittings are larger to slow the compressed air velocity down through the dryer. The piping exiting the dryer can be the same size as the air compressor connection or the outlet piping size of the dryer can be used to establish the piping downstream of the dryer.
If the ambient air conditions can drop below 32°F measures should be taken to prevent the compressed air equipment from being exposed to this as it will freeze up. During air compressor operation the most effective way to condition the room temperature is to use the heat generated by the operating air compressor(s). Excessive heat can be discharged from the room by way of a properly sized wall fan. The wall fan can be thermostatically controlled to keep the room at a constant temperature. If there are times when all of the compressed air equipment is not operating, an auxiliary heating system should be considered.
Air-cooled rotary screw air compressors reject 2545 btus/hr per horsepower. Example: A 50 horsepower air cooled rotary screw air compressor rejects 127,250 btus/hr into its surrounding environment. That is enough heat to keep a 1500 square foot home comfortable in the dead of winter with outdoor temperatures below 32°F. Many of these air compressors are installed with little thought of eliminating heat build-up around the air compressor. The heat rejected into the ambient air surrounding the air compressor is continuously cycled through the heat exchangers elevating the temperature. Unchecked, the temperature will rise to an unacceptable level, eventually overheating the air compressor & shutting it down. Ducting can be attached to the air compressor to directly route the cooling air discharge outdoors or away from the air compressor. Wall or ceiling fans can also be strategically placed in the room to exhaust the hot cooling air outside. Either way, an adequate amount of replacement cooling air must be brought into the room.
All installations have contaminants in the ambient air. Contaminants can negatively impact an air compressor in many ways. Two critical ways are indigestion into the air compressor itself with the other being fouling of the air cooled heat exchangers. The best way to determine if the air compressor is digesting an abnormally high amount of contaminants is to consistently perform oil analysis. The oil analysis should look for components not normally part of the oil make-up. The results need to be properly interpreted.
In the case of a lubricated rotary screw air compressor, all of the ambient air drawn into the machine for compression flows right past or through the airend bearings. Too much ingestion of particulate will damage the bearings. The oil not only cools the air during compression it also washes the contaminants out of the air. Over time these contaminants will build up continuing to be cycled through the bearings. For example, a 10 micron particle should be able to flow through an anti friction bearing suspended in the oil film without damaging the bearing surfaces. This does not account for multiple particles clumping together, which will damage the bearing surfaces. Two solutions for reducing digestion of contaminants are to install an air filter with a lower micron rating and higher efficiency rating. The ratings should be adjusted until the oil analysis indicates the level of contaminants is satisfactory. Remember, as the rating of the inlet air filter is increased the surface area should also be increased or the air filter may have to be changed out too frequently from excessive fouling. The second solution is to relocate the inlet air filter to a remote environment which is cleaner than the immediate area around the air compressor. The piping used to remote mount the air filter should be non-ferrous. PVC works great as it is light, easy to assemble and inexpensive. Connect it to the air compressor air end with an easily removable joint in case machine repairs or troubleshooting is required. The piping i.d. should be no smaller than the i.d. opening in the OEM supplied inlet filter mounting assembly. For every 10 feet of inlet pipe run, the pipe diameter should increase one size or 1". If the inlet air filter is relocated outdoors it should be protected from digestion of rain or snow.
Relocation of the inlet air filter is a recommended solution when the surrounding ambient area around the air compressor contains hazardous vapors or fumes. There are air filters which can remove hazardous fumes or vapors; however, they are costly to purchase and maintain.
If you’d like more information about FS-Curtis rotary screw air compressors please follow this link FS-Curtis Rotary Screw Air Compressors. I you have questions or would like more information or pricing, please visit our Distributor Lookup page on our website to locate a distributor in you area.